Most viewed tenders
Are you Looking for Joint Venture Partners, Contractor Consortium, Back-to-Back Contractor, Project Financier?
We will help you to find the right match for FREE.
Cons. And Comm. Of 200 Mm Dia T/w Providing Laying Jointing Of Pipe Line At Rwss Gothda In P.s Tijara Under Phed Div. Bhiwadi Ncr
Cons. and Comm. of 200 MM dia T/w Providing laying jointing of pipe line at RWSS Gothda In P.S Tijara under PHED Div. Bhiwadi NCR
Complete Tender Document along with addendums/ amendments issued and uploaded by the Department.
Don't have sufficient eligibility, BG funds or resources?
We will help you to find the right match for FREE.
Construction of TUBE-WELL 200 mm dia from ground levels and upto 100 mtr. Depth and above to accommodate housing and assembly pipe in all type of alluvium strata, unconsolidated formation such as pebbles, boulders etc. by percussion/ rotary drilling method as per IS:2800 (part 1 & 2) 1979 as amended up to date. The work will include cost of lowering of housing, strainer assembly pipes with supply and wrapping pf coir rope, wherever necessary and development of tubewell as per ISI specification using suitable air compressor but will not include cost of casing & strainer pipe. work will be completed after obtaining sand-free water. (a) Nominal bore 200 MM Dia.
(a) Up to 100 Mtr.
(b) Above 100 Mtr.
Construction of tube well after completion of item no. 1.0 & upto I00 mtr. depth and above in all type of rocks by DTH system as per IS : 2800 (Part I & II) 1979 as amended up to date. The work would be completed after obtaining sand free water. The tube well should have a through out bore as per nominal bore of casing pipe. (a) Nominal bore 200 MM Dia.
(a) Up to 150 Mtr.
(b) Above 150 Mtr.
Labour charges for making slots on blank pipes made of ERW MS black pipe ISI marked of following size, the slotting should be as per IS: 8110-1985. (a) 200 MM dia nominal bore of 5.4 mm thickness
Development of tube well as per IS 11189-1985 and IS: 2800 (Part-I)-1991 (both amended up to date) using suitable compressor to give sand to give sand free water for required yield of the gravel packed tube well.
Supplying and Packing pea gravel suitable for slot size/mesh size as suggested in IS:2800 (Part-I) 1991 with latest amendments.
Supply & Fixing tube well cover of MS sheet 8mm thick at top & 5 mm thick 100 mm wide shroud around the edge so as to form a cap on the topend of casing pipe with GI Nipple 45cm long & two GI flanges at bothend in 80mm sizes passing through a hole in the centre of MS sheet. A25mm socket with end plug shall also be welded over top plate (as perdrawillg enclosed). A GI nipple having outside thread of size 1/2" (forinstallation pressure gauge) shall tie provided & welded with 80mm GInipple near top plate nipple shall be provided with end plug. (a) 200 MM Dia
Supply, installation of 3 phase ISI marked submersible motor pump set of five star rating by BEE and as per IS: 8034-2018 (pump) and IS 9283- 2013 (motor) or amended upto date of approved make of following duty condition with required accessories includig making connection suitable for tube well/ DCB. The job includes lowering of motor pumps, installation of complete fitting & accessories, jointing of electrical cables upto switch board, testing of submersible pump sets and interconnection up to water mains, complete in all respect. (a) 7.5 KW (10 HP) & Head up to 120 Mtr.
Supply & fixing of ISI marked three core PVC flat submersible cable as per IS : 694:1990 ro amended upto date and conductor as per class 5 of IS 8130:1980 including making connection etc. (a) 3 core 4.00 Sq. MM
Providing & Lowering in tubewell ISI marked GI Pipe "B" class as per IS: 1239 or amended up to date threaded and double flanged (welded) on both ends and two number 25 x 3 mm flat welded on both ends between pipe & flange, rubber washer & nut bolts etc. complete in all respect. (a) 50 MM Dia
Providing and laying of GI pipe of A (light) class IS:1239 part I 2004 or amended up to date for casing pipe for submercible cable exeternal/internal work 40 mm dia complete in all respect.
Providing & Laying XLPE insulated / P.V.C. sheathed cable of 1.1 KV grade with aluminium conductor Armoured of IS:7098-I/1554-1 approved make in ground as per IS:1255 including excavation of 30cmx75cm size trench, 25 cm thick under layer of sand, second Class bricks covering, refilling earth, compaction of earth, making necessary connection, testing etc. as required of size. (a) 4 core 16.00 Sq. MM
Providing & Fixing double flanged, CI body ISI marked NRV of Approved make of Size. (a) 80 MM Dia
Supply and Fixing of CI D/F Sluice Valve of 80 MM as per specification including cost of labour jointing material with nuts bolts and rubber sheets etc. complete
Providing and Fixing of 80 mm G.I. pipe from above upper end of well cap water meter up to sluice valve (Min 2 Mtr away from Tubewell from tubewell pipe) rising main from ground level. Includiding All accessories (Socket GI/ Flanges/ Bends/ as per specification including earthwork as directed by EIC.
Supply & installation of 100 mm diameter sealed diaphragm bourdon type pressure gauge og range 0 to 10 kg. including all jointing material as per specification with safety cover.
Providing, Installing, testing and commissioning of double flanged Bulk water meter with removable machanism of class B confroming to ISO 4064/1 or amended up to date of approved make icluding cost of all material and labour as per specification with G.I box (sheet16 SWG) sutabile with locking arrangment of dia. (a) 80 MM Dia
Supply and Fixing of electric control feeder panel comprising of suitable rating MCCB , fully automatic star-delta starter, over load relay, ampere meter with CTs, volt meter, phase preventor, suitable starting capacitors,phase indicators, lighting arrangement etc complete suitable for three phase pump set. The panel should have space for energy meter (supplied by DISCOM). All these equipments shall be housed by panel box made out from 18 guage M.S. Sheet with powdercoating.Panel should be of minimum size 900 x 600 x 450 mm with Stand ( made of angle iron of size 35x35x5mm) duly bolted/screwed with enclosure box having 4 legs,each leg's length 18" and double door including in built locking system. The legs should be embedded in M-15 cement concrete plat form.The size of CC plateform should be equal or bigger than the base size of panelhaving height of at least 200 mm from ground level. The panel should have opening of suitable size in front of space for energy meter with glassfor meter reading. The operation of panel should be suitable for on 440Volt AC Supply. (a) above 10 HP and Up to 15 HP